for Southern Pines, NC
Paul - Southern Pines, NC
concerned that Ed tells us he has to replace a wire to the compressor the apparently overheats because of the current draw. Why is this ?
Paul - Southern Pines, NC
Pleasant young man. Nice to talk to.
Please return to finish
Tanya - Southern Pines, NC
I need to have you return next week to finish installing the registers. The head person doing the installing was very good. The workers were pleasant.
Polite, on time, good worker
James - Southern Pines, NC
John - Southern Pines, NC
Sandra - Southern Pines, NC
I appreciated the information given to me during the visit. I learned things I had never been told before.
Baccinelli - Southern Pines, NC
Tim, and the crew of 72 Degrees was of awesome assistance when I needed them most.
Very prompt, efficient and knowledgeable
Coggins,Virginia - Southern Pines, NC
Don was great
Ian - Southern Pines, NC
Don was professional,technically proficient, and offered great solutions to current and foreseeable problems.
Repair Heat Pump & Install Pan Treatment device in Furnace
Charles - Southern Pines, NC
The Technician that called on me was very knowledgeable and helpful. He repaired my heat pump by replacing a defective capacitor in about 15 - 20 minutes. Cost $0.00, as I have a 10 year Parts & Labor contract with 72 Degrees -- who installed my new Heat Pump & Furnace in 2009. When he finished that repair I inquired about the recommended need to flush the furnace 'discharge line' with bleach. He informed me that something was available to install in the Furnace to totally eliminate the necessity for this. He referred to it as a Pan Treatment device and indicated he had one in his truck. I requested that he install the device, which he did in less than 1/2 hour. Cost $79.95 -- so that is one less thing I have to be concerned about in the future. I was very pleased with his service, and the assistance of the Ladies in the 72 Degrees Office, in Sanford NC, who always strive to put a smile on their customers faces. MISSION ACCOMPLISHED!!! Thanks
Installed safety switches at air handler!
Fall maintenance on a Goodman heat pump!
Spring maintenance on a new Rheem heat pump!
Spring maintenance on 2 Trane units!
Winter maintenance on 2 Trane units. Reccomend UV lights for both units!
Winter maintenance on a Amana heat pump!
Diag on a Rheem heat pump. Breaker tripped in the crawl space
Comfort check on a Rheem unit
Diag on a Amana heat pump
Spring tune up on a Amana heat pump.
Tune up on 2 Trane units.
Tune up on a Goodman unit
INSTALLER B .
Repair duct work and leak test
Preventative maintenance on a Goodman heat pump system
Called out for air handler leaking onto attic in ceiling in home. Reworked drain line on second floor system, found system low on refrigerant and added 2 pounds of r22. Customer is now aware of leak.
Service call to fix AC blowing hot air under warranty. Found that furnace was running with ac. Verified that thermostat was set up correctly. System was on a zone system before but zone board has been bypassed. Removed low voltage wires from thermostat that is not being used to make sure that this wasn't causing heat to come on. Went to board to check wiring and furnace went out upon moving wires. Repositioned wires to verify that w1 was not being energized on call for cooling. Reset system multiple times in heat and cool. System is operating as needed at this time.
Replaced heat strip kit & contactor on heat pump.
cleaned and serviced Amana heat pump
Performing spring maintaince on a Amana heat pump.
Performing spring maintaince on Amana heat pump